Based on recent Underwriters Laboratories Inc. (UL) and FM Approvals “witnessed” testing, the minimum Class A extinguishing concentration for 3M™ Novec™ 1230 Fire Protection Fluid was reduced from 3.5% to 3.3% for all systems that meet the minimum average nozzle pressure of 74.4 psi. Because the design concentration for Class A hazards is directly impacted by the heptane cup burner values, the test result will not impact the design concentration for Class A hazards.
The testing, however, will reduce the minimum design concentration for National Fire Protection Association (NFPA) 2001 Class C energized hazards from 4.7% to 4.5%,* resulting in a potential 4.25% reduction in the amount of agent required for Class C hazards.
The reduction in Novec 1230 fluid extinguishing concentration is the direct result of 3M’s efforts to validate the fluid’s efficiency and performance – just one more reason to choose the sustainable, smart solution: 3M™ Novec™ 1230 Fire Protection Fluid.
Unlike the potent greenhouse gases HFC-227ea (Chemours’ FM-200™) or HFC-125 (Chemours’ FE-25™), Novec 1230 fluid is not targeted for phase-down under the European F-gas regulation and is not subject to the global HFC phase-down under the Kigali Amendment to the Montreal Protocol. Also, under the Significant New Alternatives Policy (SNAP) Program, the U.S. Environmental Protection Agency (EPA) has proposed a status change for HFCs sold into various industry sectors.
• 3.3% x 1.35 = 4.5% - Class C minimum design concentration is 1.35 times the Class A minimum extinguishing concentration (UL 2166, UL 2127).
©3M 2017. All rights reserved.
3M and Novec are trademarks of 3M Company.
FM-200 and FE-25 are trademarks of The Chemours Company FC, LLC.
All other trademarks are properties of their respective owners.
Get the next quarterly issue of 3M’s Fire Wire newsletter in your inbox and keep up to date on the latest fire suppression industry news from 3M.